Ask a tradesman
Reloaction of electric meter
We have just bought a house,and the exsisting Electric meter+Fusebox are right in the Lounge,which is looking like an eye sore,We are keeing it there and making a box as last option,its hanging on the inside of the boundary wall,My question is have we got the option of Ripping everything from its current location and putting in at the same postion but ouside the wall,In a water proof box?I have seen these boxes online and they are not very expesive either,there is no distance involved,Just putting outside.
Can a qualified electrician do it?or i need to get the supplier involved,I have heard they charge a lot,Should I use it as bargain tool with diffrent Supplier if they try to charge me ?
There is NO DIGGING or extending the cable required,just wants it to be from inside of the wall to outside of the wall,exactly behind the exsisting meter,just on the otherside of the wall
2 Answers from MyBuilder Electricians
Relocating the meter and the fusebox is only part of the job. To relocate the incoming supply cable from the road, you need to speak to the connections department of the Distribution Network Operator for you area. The incoming cable belongs to them and is only rented out to the supplier. It typically costs between one to two thousand pounds to get this cable reclocated by the DNO, even though the cable you have is long enough and does not need extending, the Electricity at work Regulations 1989 require that the cable is made dead and safe to work on first, to do this it must be cut outside (as the whole street can not simply be turned off!) to do this a hole on the footpath outside needs to be dug up and the incoming cable cut so its dead and safe for the cable jointer from the DNO to work on safely. It may also disrupt your front garden/drive depending on where they need to dig. Added to this you will have to pay your own electrician to alter your internal house wiring and fit a new BS7671 17th edition fusebox, plus notify building control under part P of the building regulations. Overall allow about £3000 for the works in total.
Hope this helps.
Answered 3rd Jan 2012
To relocate the main it is a big job and it is expensive. It is always a solution With some alteration and half of the price you still can complete the work and comply with regulation and register with the building control through the NICEIC.
Answered 4th Jan 2012
Location of electric cooker - need to stand with back to the side of the cooker to open fridge door
My son in law has just rearranged his kitchen am I am concerned about the position of his electric cooker. The kitchen is around...
Electric sub meter installation?
i have one meter (mpan) but am in the process of selling the two properties that in effect both use it (the meter itself is a long...
Move electric meter to external wall which isn't yet built
Hi all, I'm having a double storey extension side extension done later in the year and part of the work being done is knocking...
Fitter refusing to connect gas hob as gas meter is too close to electric
The title says it all really. I had a new replacement gas hob and boiler fitted to an existing installation by a local Gas...
Post your job to find high quality tradesmen and get free quotes
- All Questions
- Architectural Services
- Bathroom Fitting
- Carpentry & Joinery
- Carpet & Lino
- Central Heating
- Chimneys & Fireplaces
- Conversions - General
- Damp Proofing
- Demolition & Waste Clearance
- Fascias, Soffits & Guttering
- Gas Work
- Groundwork & Foundations
- Hard Flooring
- Kitchen Fitting
- Landscape Gardening
- Loft Conversions
- New Builds
- Painting & Decorating
- Restoration & Refurbishment
- Security Systems
- Tree Surgery