Ask a tradesman
Fitting of gas boiler when no gas connection
The house I am moving in to has no gas but can be connected as the rest of the street has it. Is it possible to have a boiler and whole CH system installed before the connection from the mains to the house is completed as this is going to take around 6 - 8 weeks.
Additionally, the gas company wants to know how many meters from the road the gas pipe needs to go, so the further it is the more expensive. Therefore is it possible to have the mains go to the front of the house and then the installer to run the plumbing from there to the back of the house where the boiler is to be installed?
Kind regards John
2 Answers from MyBuilder Gas Engineers
Southsea • Member since 8 Nov 2010 • 231 jobs, 99% positive feedback
A simple answer YES !
We carry out alot of these types of installations, prior to the mains gas to the property being connected.
Everything can be checked on the wet side of the heating system. The gas line can be pressure tested with air from the proposed meter position to the new boiler position.
The gas meter would generally be located at the nearest point to the road supply, as you suggest.
The installer would carry out a gas pipe-work size calculation to determine what size pipe-work should be used around / through the building.
Typically the new pipe would be run from the proposed new meter position, to the first floor, through the floor joists to the new boiler. Or maybe around the outside of the house if the new boiler is in ground floor kitchen / utilit area.
In an event, please post the job on this site so you maybe able to get the ball rolling.
Answered 29th Dec 2011
Yes it is possible to fit but obviously it will not be working and the commisioning of the boiler will have to be done when gas is available, you will have to discuss with your gas provider or National Grid to discuss where your meter is to be fitted so that the gas run can be fitted.
Answered 29th Dec 2011
Fitting a Gas cooker / gas supply to it + a few more gas related question
Hi, I'm about to buy a property (located in NE England) and embark on a pretty major refurbishment of the kitchen area and...
Can you get a Gas Safety Certificate when a decomissioned back boiler remains in place?
Hello, I have a house which I bought several years ago and now rent out (after living in it for 3 years myself). It has a...
supply pipe to new combi boiler with 15mm inlet gas connection
Hi, I recently had a glow worm ultimate 30c combi boiler fitted by a gas safe registered fitter. I want to enquire whether it has...
New Boiler - can I have a new boiler fitted if there is a a small gas leak?
Hi there, Question – can I have a new boiler installed if there is a “small gas leak” but within the permissible drop?...
Post your job to find high quality tradesmen and get free quotes
- All Questions
- Architectural Services
- Bathroom Fitting
- Carpentry & Joinery
- Carpet & Lino
- Central Heating
- Chimneys & Fireplaces
- Conversions - General
- Damp Proofing
- Demolition & Waste Clearance
- Fascias, Soffits & Guttering
- Gas Work
- Groundwork & Foundations
- Hard Flooring
- Kitchen Fitting
- Landscape Gardening
- Loft Conversions
- New Builds
- Painting & Decorating
- Restoration & Refurbishment
- Security Systems
- Tree Surgery