Ask a tradesman
Is it safe to run pvc trunking through a bathroom
I need to run five 6mm cables in a commercial property. The shortest way would be to run them in surface mounted trunking through the bathroom.
This would follow the wall around at ceiling level at a height of 2.4 metres.
In the safe zone.
The only thing I am worried about is that part of the trunking would be over but well above a shower unit.
There would be no breaks in or connections to the trunking within the bathroom.
3 Answers from MyBuilder Electricians
Firstly, a kitchen is not a special location. And secondly, wiring in surface trunking has nothing whatsoever to do with Zones and can run anywhere. The zones are only relevant when it comes to final circuit terminations and switchgear, and what zone it can be placed in is determined by each piece of equipment.
All circuits running through bathrooms should now be protected by RCD though, that is correct.
Answered 16th Nov 2015
Here is a link to the IET website that explains the requirements of electrical installations in locations containing a bath or a shower.
There is also a downloadable PDF on the above website for further information.
Hope this helps!
Domestic Power Services
Answered 11th Nov 2015
All wires running through "special Locations" (Kitchen & Bathrooms) must be protected by an RCD. So long as the trunking is outside the zones it's ok. But it won't look nice!
Answered 12th Nov 2015
at my mums property when water is run from bathroom taps there is a strong eggy smell in her kitchen beneath, have checked to see if water is running freely with dye which comes through straight away
the soil pipe is boxed in under built in furniture, pipework for basin was new when this put in, smell is not there when wc is...
Is there a 3 PHASE inverter out there that can manage a possible output of up to 60.000 watts for a tanning shop?
I know we can change the power supply via energy company but this is been quoted as a 6 week minimum wait and would rather get set...
Buying a house with a gas meter in bathroom? Is it safe? How much to get it moved?
We've had an offer accepted on a 5 bed Victorian terrace house that needs work. We're keen to get the CH looked at before we...
Is it safe to run a mains cable across a cupboard threshold?
In our near-complete loft conversion, there is an eaves storage space, accessed by two low doors. An electrical cable, I guess...
Post your job to find high quality tradesmen and get free quotes
- All Questions
- Architectural Services
- Bathroom Fitting
- Carpentry & Joinery
- Carpet & Lino
- Central Heating
- Chimneys & Fireplaces
- Conversions - General
- Damp Proofing
- Demolition & Waste Clearance
- Fascias, Soffits & Guttering
- Gas Work
- Groundwork & Foundations
- Hard Flooring
- Kitchen Fitting
- Landscape Gardening
- Loft Conversions
- New Builds
- Painting & Decorating
- Restoration & Refurbishment
- Security Systems
- Tree Surgery