Ask a tradesman
Radiator not getting hot, how can i fix it?
HELP!!!! we have recently decorated the whole house and took off all the rads and painted behind them, we have them all working apart from one. the rad thats not working is directly below another thats hot. the pipe that runs down from the working rad is cold. I have tried blleding the rad, shutting off all rads apart from this one and still freezing cold. i am lost as to what to do next, anyone able to help?
I have already turned off all the rads apart from the one not working and also bled the rad still not working
Just a update, I took the TRV off and the pin is fine. There are no air locks as I have bled all the rads. Sorry anymore suggestions, the pipes are not even getting warm
Update number 2.
I drained the water out and the pipe and rad started to get warm, but after I stopped this the rad was cold again. Could one end of the rad be faulty? Anymore suggestions
2 Answers from MyBuilder Plumbers
Hi mate sounds like its air locked. Turn off all the other rads in the house and that should push the air through.
If its got a TRV remove the head and check the pin is not jammed down. Sounds stupid but check both valves are on
Answered 4th Dec 2012
If you have a drain off on the pipework try draining water out to drag the heat to the rad. If you don't have a drain off get a bucket and open the air vent plug and allow the water to run into the bucket until it gets warm. Hopefully this will get the heat to the rad and once its there it should be able to find its own way back.
Answered 6th Dec 2012
Post your job to find high quality tradesmen and get free quotes
- All Questions
- Architectural Services
- Bathroom Fitting
- Carpentry & Joinery
- Carpet & Lino
- Central Heating
- Chimneys & Fireplaces
- Conversions - General
- Damp Proofing
- Demolition & Waste Clearance
- Fascias, Soffits & Guttering
- Gas Work
- Groundwork & Foundations
- Hard Flooring
- Kitchen Fitting
- Landscape Gardening
- Loft Conversions
- New Builds
- Painting & Decorating
- Restoration & Refurbishment
- Security Systems
- Tree Surgery
- Can I paper on top over Laura Ashley paper that has thin wipeable vinyl top layer but is not peelable ? Or how can I strip it without also removing the crosslining paper below?
- Radiator removed, system drained. Combi boiler can I have hot water?
- One radiator not getting hot, how can i fix it?
- Do I have to insulate solid walls? Can I not and just insulate rest of house.