Ask a tradesman
I need to box in a boiler, how much space do i need??
I'm doing a job, boxing in a combi boiler and have had concerns about how much ventilation it needs. Its a vaillant eco max combi boiler and have spoke to the guys at vaillant and was informed that as its a combi boiler it doesn't need ventilation, However, they did say there needs to be a minimum of 500mm from the front of the boiler, to the doors that access it for servicing reasons. The problem is this can't be done as the boxing will be massive and will just look utter rubbish in the area it is in. (is this a strict guidline that needs to be stuck to??)
My girlfriend not long ago had a new vaillant combi boiler fitted in an existing boxed in area with door and the space between the boxing door and the boiler is only 200mm and it was fitted by gas safe engineers obviously.
On this job, i can only have a gap of 100mm max and i just can't see why that if its not a ventilation issue and only for servicing reasons, why i can just put some doors on it, and removable shelves below so that it can easily be got at if i ever needs servicing.
the guy i'm doing the job for has left it to my discretion so, obviously i don't want to get this wrong.
Any help would be appreciated.
4 Answers from MyBuilder Gas Engineers
Chesterfield Mansfield • Member since 23 Mar 2010 • 539 jobs, 100% positive feedback
i think you have misunderstood what the valliant seviceteam are saying ,take a look in the installation instructions ,you can fit a door infront of the boiler with as little as 5mm clearance but need 500mm when the door is open to access the boiler ,would need probably 200mm below and above and 5mm either side as a rough guess
Answered 2nd May 2011
Hi there,the space they are talking about is so that an enginner can get access to the front casing so you can have a door practically touching the boiler casing.
If you have the instructions at hand they will guide you as to space required on either side of the boiler as well.....
Answered 2nd May 2011
Newcastle Upon Tyne • Member since 23 Mar 2009 • 13 jobs, 85% positive feedback
You can fit the boiler into a unit but the service engineer will need to access to the front access panel of the boiler for servicing. Ventilation is not the issue.
Answered 3rd May 2011
- i want to put a window in a small bathroom do i need permission ? and would i need to put a lintel in as its a flat roof
Where do I start with planning a single storey extension? How much should I be paying for architects plans?
I live in an average sized semi detatched house. I am planning a small single storey extension at the side of my house (approx 10m...
- i have cental heating in my house and i want a gas fire, i have no chimney or ventilation so i have been told i need a flueless gas fire how do i get a flue fitted
How much work do I need to do to be 'Satisfactory'
In order to satisfy my home insurance company, I recently had a NICEIC inspection on my recently purchased house (that I will be...
Post your job to find high quality tradesmen and get free quotes
- All Questions
- Architectural Services
- Bathroom Fitting
- Carpentry & Joinery
- Carpet & Lino
- Central Heating
- Chimneys & Fireplaces
- Conversions - General
- Damp Proofing
- Demolition & Waste Clearance
- Fascias, Soffits & Guttering
- Gas Work
- Groundwork & Foundations
- Hard Flooring
- Kitchen Fitting
- Landscape Gardening
- Loft Conversions
- New Builds
- Painting & Decorating
- Restoration & Refurbishment
- Security Systems
- Tree Surgery