Ask a tradesman
Tripped lights - not working after we have turned it back on at the fuse box
The lights in our sitting room have tripped, we turned them back on at the fuse box. But still the lights don't work, all the bulbs have "gone" - there were 5 bulbs. When we try & put new bulbs in it trips the electrics again. Any advice would be welcome.. :)
3 Answers from MyBuilder Electricians
due you e saver lamps, if one is fault this will course it to trip.
Answered 12th Nov 2012
Is it the R.C.D or the breaker that’s tripping out?
Firstly remove the lamps (bulbs) from each fitting. A blown lamp can cause this depending on how it blows. Then see if the power stays on. If not ensure all light switches are off then try again.
If the power stays on try each lamp at one light fitting to test it.
If the power won’t come on then there’s a fault within the circuit.
This should be an easy job for an Electrician.
Hopefully it’s a faulty bulb. Hope this helps
Answered 12th Nov 2012
If its the RCD thats tripping then its either a neutral to earth or live to earth fault. Not easy to check without a test meter, but should be an easy fix for an electrician.
Answered 13th Nov 2012
Post your job to find high quality tradesmen and get free quotes
- All Questions
- Architectural Services
- Bathroom Fitting
- Carpentry & Joinery
- Carpet & Lino
- Central Heating
- Chimneys & Fireplaces
- Conversions - General
- Damp Proofing
- Demolition & Waste Clearance
- Fascias, Soffits & Guttering
- Gas Work
- Groundwork & Foundations
- Hard Flooring
- Kitchen Fitting
- Landscape Gardening
- Loft Conversions
- New Builds
- Painting & Decorating
- Restoration & Refurbishment
- Security Systems
- Tree Surgery
- I have problem with my CH whereby first thing in the morning when the heating comes on it doesn't switch off when the thermostat temp setting is reached and continues to heat the house.
- We have our double garage converted to have an office and an utility room (two seperate rooms). We did not get the electric certificate and the building certificate for the work done already.
- Intermittent central heating fault on Baxi Duotec
- Lights in bedrooms won't work after fuse tripped but bathroom light works - how can one light out of four on the same circuit work?