Ask a tradesman
Hi there, i need to box in a boiler, however how much ventilation does it need??
As the space it is in, is of an usual size it means i'm going to have to make the door myself out of 18mm m.d.f or ply, but i'm worried there will no ventilation going in and out. Is it possible to just put some plastics vents into the boxing and if so how many? Any help would be appreciated. Cheers
3 Answers from MyBuilder Gas Engineers
Blackheath • Member since 31 Dec 2009 • 566 jobs, 100% positive feedback
The amount of ventilation required will vary depending on if your boiler has an open flue,a balanced flue or a room sealed flue.Ventilation requirements vary vastly so if i were you i would contact the boiler manufacturer and ask their advice or go on the internet and source the information.All boilers have a GC number.Gas Council number.This is a seven digit number that is displayed on the data badge on the inside casing of the boiler.This is the models exact make.With this information you can go online and source the ventilation requirements for your boiler.Older boilers will require HIGH AND LOW VENTILATION.NON CLOSEABLE AND NON FLY SCREENED WITH MINIMUM HOLE SIZES OF 5MM PER HOLE.Most people don`t realise that if a boiler overheats in a cupboard and burns a house down that ignorance might affect your house insurance.Lastly ,new condensing boilers normally don`t need ventilation requirements as they run cool BUT WILL REQUIRE AROUND 5MM ON THE SIDES AND AROUND 150 MM TOP AND BOTTOM FOR SERVICING
Answered 19th Jan 2018
Loughton • Member since 26 Apr 2011 • 4 jobs, 100% positive feedback
Always refer to the boilers mi manurfacturs instructions ,if lost then google model numbers for specs ,if old open vented type do not box in !! with out reading mi ,and consult a gas safe fitter ,
Answered 26th Apr 2011
I need to box in a boiler, how much space do i need??
Hi there, I'm doing a job, boxing in a combi boiler and have had concerns about how much ventilation it needs. Its a...
Fitting a Gas cooker / gas supply to it + a few more gas related question
Hi, I'm about to buy a property (located in NE England) and embark on a pretty major refurbishment of the kitchen area and...
- I need to replace a bath shower/ tap mixer. There is a side bath panel which I was not able to remove myself. I would like to get a side panel fitted afterwards. How much would it cost?
New Boiler - can I have a new boiler fitted if there is a a small gas leak?
Hi there, Question – can I have a new boiler installed if there is a “small gas leak” but within the permissible drop?...
Post your job to find high quality tradesmen and get free quotes
- All Questions
- Architectural Services
- Bathroom Fitting
- Carpentry & Joinery
- Carpet & Lino
- Central Heating
- Chimneys & Fireplaces
- Conversions - General
- Damp Proofing
- Demolition & Waste Clearance
- Fascias, Soffits & Guttering
- Gas Work
- Groundwork & Foundations
- Hard Flooring
- Kitchen Fitting
- Landscape Gardening
- Loft Conversions
- New Builds
- Painting & Decorating
- Restoration & Refurbishment
- Security Systems
- Tree Surgery