Ask a tradesman
No water from hot taps
I have an open vented system. The flow of water from my hot taps lessened over a few hours and then just stopped. There is no hot water coming from any hot tap. All cold taps are working.
Initially I thought this was an airllock. But I have forced mains water from the garden hose pipe back through every hot tap. There is no burbling and the hot water does not start to flow through.
The cold water loft tank is full. The hot water cylinder appears to be full. I have blown back through the open vent pipe at the cold water tank which runs from the T junction above the hot water cylinder to the cold water tank. The air does not go into the cylinder but bypasses it and comes out of an open hot tap. So the pipe appears to be clear.
In the cold water tank in the loft the inlet to the downpipe at the bottom of the tank which is the cold water feed to the hot water cylinder appears to be clear.
I have a power shower which takes water off the hot water cylinder from a different outlet to the taps, at about 3/4 of the way up the cylinder. (The tap outlet is at the top). However when I do this I "think" it creates a gap at the top of the hot water cylinder as at this point I can then force water from my hose pipe back though a hot tap and I can feel the water outlet pipe at the top of the hot water cylinder go cold and water splashing into the tank.
i am not a plumber, just a DIY guy. My guess is that there is not enough pressure to push any hot water out of the top of the hot water cylinder to the taps. This may be caused by a blockage in the cold water feed, as the hot water cylinder is not refilling quick enough to keep it full and maintain pressure. The blockage may only be partial as the tank appears to be full, but could be filling slowly.
I would be grateful for any advice as to whether you think this is the issue or whether it could be something else. How do I confirm this. What is the best way to clear a blockage.
Thank you in anticipation of your help.
2 Answers from MyBuilder Plumbers
New Romney • Member since 15 Nov 2016 • 32 jobs, 100% positive feedback
cold feed to cylinder may be blocked where it enters cylinder,if the cylinder is old it may be blocked with scale.
Answered 23rd Feb 2019
No water from hot taps, hot water tank empty
I have no water coming from my hot taps at all - cold water works fine. It looks like the hot tank is empty - we don't have a...
No water coming from any hot water taps
Hi. The water tank in the loft leaked which was sorted. The following day after using the shower the ball cock has broken which...
No hot water on combi. Re-pressurised boilder but now no water from hot taps
I noticed the water not heating up when doing the washing up. I went to look at the boiler (an old Potterton) to see it was...
Taps taps taps taps taps taps taps taps taps taps taps taps
So my tap keeps blowing then leaks I've changed the gland 3 times it's working for about 2 3 days then the same happens again
Post your job to find high quality tradesmen and get free quotes
- All Questions
- Architectural Services
- Bathroom Fitting
- Carpentry & Joinery
- Carpet & Lino
- Central Heating
- Chimneys & Fireplaces
- Conversions - General
- Damp Proofing
- Demolition & Waste Clearance
- Fascias, Soffits & Guttering
- Gas Work
- Groundwork & Foundations
- Hard Flooring
- Kitchen Fitting
- Landscape Gardening
- Loft Conversions
- New Builds
- Painting & Decorating
- Restoration & Refurbishment
- Security Systems
- Tree Surgery