Ask a tradesman
Rcd tripping when appliance is switched on.
I have a spur circuit off the distribution board. When I plug in and switch on an appliance, it trips the RCD. It's done it with a drill and with a vacuum cleaner, both of which cause no problem on the ring main.
I've re-wired the spur (it's only about 2m from the board), and it's still the same.
I've replaced the MCB on the circuit with a bigger one, and it's the same.
2 Answers from MyBuilder Electricians
So you changed the mcb for a bigger one, even though it’s the RCD that is tripping? You are putting yourself in danger by doing this as the mcb trips on overload and the RCD trips on an earth leakage fault between live and neutral. By upping the rating on the mcb the cable could overheat and possibly burn your house down. I would strongly recommend you get an electrician in with test equipment to check all this out. It’s highly unlikely to be a faulty RCD or mcb. As it’s a diy job I think you may have something wrong, all circuits are dead tested BEFORE energising when a professional does it.
Answered 15th Sep 2018
It could be earth leakage
If the hole house is on one RCD the earth leakage could be on a different circuit but when your putting your appliances on it could be just enough to push the RCD to trip.
Best way to solve this issue is to get a registered electrician to put an earth clamp meter on and find out if this is the issue then if so to narrow it down and find the culprit.
Answered 16th Sep 2018
Why would RCD trip when I cut a wire on a circuit where MCB is switched off?
I'm changing a single socket for a double socket in the garage, and I needed to shorten the cable a little. The RCBO for the...
RCD tripping when Heating on?
Hello, Following visit from two very skilful electricians I thought Id post my question here as I am looking for some...
Why does my washer keep tripping all the electrics in the house?
*update Nov* This is still unresolved. Electrician is bow going to try putting a new box in with seperate RCDs for each circuit...
Both my showers (upstairs and downstairs) are tripping the rcd switch when the shower is turned on?
As above I found the problem. We have outside lights and water had got into one of them. Now iv isolated them. The showers are...
Post your job to find high quality tradesmen and get free quotes
- All Questions
- Architectural Services
- Bathroom Fitting
- Carpentry & Joinery
- Carpet & Lino
- Central Heating
- Chimneys & Fireplaces
- Conversions - General
- Damp Proofing
- Demolition & Waste Clearance
- Fascias, Soffits & Guttering
- Gas Work
- Groundwork & Foundations
- Hard Flooring
- Kitchen Fitting
- Landscape Gardening
- Loft Conversions
- New Builds
- Painting & Decorating
- Restoration & Refurbishment
- Security Systems
- Tree Surgery