Ask a tradesman
Help - cold water tank in loft water level decreases when no water is used
2 floor Victorian house with a cold water tank in the loft. no 2nd floor bathroom, bathroom moved to down stair extension (is like this when we got the property).
Recently, been told our meter is constantly running and suspect possible leaks. One of them could relating to this cold water tank, been told to check ballcock valve etc, all looks fine, water stops when you lift the ball valve upward. No water drips or wet patches anywhere.
Until I was curious and hold the ball valve upward for 10 mins, to be concern the water level of the cold water tank decreases....!! help!!!
What does this implies? internally leaking to where???
2 Answers from MyBuilder Plumbers
New Romney • Member since 15 Nov 2016 • 32 jobs, 100% positive feedback
under ground floor,have you checked your toilet it may have internal overflow allowing water to flow into toilet bowl.
Answered 27th Aug 2018
Lymington • Member since 27 Apr 2016 • 16 jobs, 94% positive feedback
Yes, as D&R said the WC is a good thing to check, however you could have an underfloor leak.
Another thing to check if you have a gravity fed heating system is there is no overflow from the small header tank if it's at a lower level than the main tank. What you are looking for if this is the case is perforation of the HW cylinder heat exchanger. If it is overflowing from the small tank then tie up the ballvalves or close the service valve to the main tank & leave it till the water level stops dropping. The level in the main tank should now be the same as the surface level in the small tank, = perforated heat exchanger. Whilst you conduct the latter test, also check your water meter. If it's still moving then you have a secondary problem too.
Answered 19th Sep 2018
No water coming from any hot water taps
Hi. The water tank in the loft leaked which was sorted. The following day after using the shower the ball cock has broken which...
Hot water being back flowing into Cold water tank
Any advice would be extremely appreciated. I have an indirect heating system. A few days ago the large cold water tank overflow...
No water from hot taps
I have an open vented system. The flow of water from my hot taps lessened over a few hours and then just stopped. There is no hot...
Cold water keeps getting an air lock following cholorination of cold water tank
As part of landlord regulations I had to get cold water tank chlorinated. I used local recommended plumber. The tank was cleaned...
Post your job to find high quality tradesmen and get free quotes
- All Questions
- Architectural Services
- Bathroom Fitting
- Carpentry & Joinery
- Carpet & Lino
- Central Heating
- Chimneys & Fireplaces
- Conversions - General
- Damp Proofing
- Demolition & Waste Clearance
- Fascias, Soffits & Guttering
- Gas Work
- Groundwork & Foundations
- Hard Flooring
- Kitchen Fitting
- Landscape Gardening
- Loft Conversions
- New Builds
- Painting & Decorating
- Restoration & Refurbishment
- Security Systems
- Tree Surgery