Ask a tradesman
I need to replace my boiler. when he came to fit it, he said that it has a 15mm inlet pipe and the new valiant needs a 28mm pipe. is this correct?
Correction: it's 22mm not 28.
6 Answers from MyBuilder Gas Engineers
the boiler needs a supply of gas as dictated by the the gas supply. it is all about pipe sizing for the property and the need of all appliances
Answered 21st Oct 2011
Ashton Under Lyne • Member since 14 Apr 2011 • 33 jobs, 100% positive feedback
i have never known any domestic boiler ever to have a 28mm gas conection at the boiler!!!22mm or 15mm yes.tom clydebank plumbing&heating
Answered 23rd Sep 2011
Blackpool • Member since 12 Nov 2010 • 10 jobs, 100% positive feedback
he may mean 28mm from the gas meter end depending how far the distance is from the meter to the boiler
Answered 25th Sep 2011
Yes, I agree. He is talking about upgrading the size of the pipe from the gas meter to the boiler as the 15mm pipe may not deliver enough gas to your new boiler. This is very common these days.
Answered 26th Sep 2011
This does sound very normal to upgrade your domestic gas inlet supply to 22mm. Depending on which boiler you replace the existing with, not model 'Vailaint' as you mentioned but style. For example a 'combi boiler' would draw off more gas in a shorter period of time as the hot water is instantaneously heated, as opposed to a 'heat only' or 'system boiler' where they would heat a HW cylinder over a period up to an hour. Little behold to upsize a 15mm gas pipe to 22mm is not a difficult job. Hope this helps. DC Plumbing & Heating.
Answered 28th Dec 2014
MAKES NO DIFFERENCE about boiler and pipe sizing... its about the volume of gas and how many meters the gas box is away and valiant do show clearly in there book (off the top of my head) that it requires 19 mb so it is completely common to need 28mm gas pipe!
Answered 28th May 2015
Is it standard procedure for plumber to keep charging to pick up parts?
Hi I had a plumber in as I had leak in my property and my boiler pressure was zero so thought it was cause. When I first rang...
New boiler fitted on the benchmark it says system was flushed with TF3
Hiya thanks for reply on boiler that may need flushed. My argument is that I am aware of the pressure dropping is due to a leak....
New Boiler - can I have a new boiler fitted if there is a a small gas leak?
Hi there, Question – can I have a new boiler installed if there is a “small gas leak” but within the permissible drop?...
Is it acceptable to do work for a client that has not been agreed and then demand payment?
I have just had a kitchen fitted by a general builder who I had used previously for one job. This gentleman had gained my trust...
Post your job to find high quality tradesmen and get free quotes
- All Questions
- Architectural Services
- Bathroom Fitting
- Carpentry & Joinery
- Carpet & Lino
- Central Heating
- Chimneys & Fireplaces
- Conversions - General
- Damp Proofing
- Demolition & Waste Clearance
- Fascias, Soffits & Guttering
- Gas Work
- Groundwork & Foundations
- Hard Flooring
- Kitchen Fitting
- Landscape Gardening
- Loft Conversions
- New Builds
- Painting & Decorating
- Restoration & Refurbishment
- Security Systems
- Tree Surgery