Ask a tradesman
My property was renovated in 2003 as was the electrical installation, the certificate issued has long gone. If there is now a new inspection this would highlight the differences in the regulations, mainly the introduction of every circuit to be protected with rccb's or rcbo's and such. Is the work mandatory if an inspection report were required.
3 Answers from MyBuilder Electricians
Accrington • Member since 16 Dec 2010 • 33 jobs, 100% positive feedback
No, could only be listed as C3 a recommended upgrade at most.
Answered 11th Oct 2015
Bodmin Moor • Member since 4 Sep 2015 • 9 jobs, 100% positive feedback
No, nothing is mandatory. The only potentially mandatory situation is that an inspecting electrician make safe something which is not, where to NOT do so would be negligent. However, at least, they must inform you and explain to you the really dangerous situation. You could then, switch everything off as it were and organise your own repairs elsewhere. The electrician probably won't continue until that part is made safe.
The inspection may advise you of a number of C1, C2, C3 hazards. C1 Danger Present, C2 Potentially dangerous, C3 Improvement recommended. These are based on 'observations' of what is inspected and tested. So, it may be observed that a consumer unit "does accord with the current IEE Wiring Regulations" or "is damaged" for instance, but should not read "consumer unit must be replaced".
You do not have to upgrade anything just because a new edition of the IEE Wiring regs is in force. But you may be advised that 'observations' have been made which highlight certain hazards exist.
Answered 11th Oct 2015
The only area that might cause a classification code of C2 (potentially dangerous), assuming that the supplementary bonding in the bathroom is in place, is if socket outlets that may reasonably be expected to be used to supply portable/mobile equipment outdoors haven't got RCD protection. (Ground floor sockets)
I would highly recommend that these sockets, if they haven't already, have additional 30mA RCD protection.
Answered 12th Oct 2015
I am renting my flat out for the first time and have just had an Domestic Electrical Installation Periodic Inspection Report. I was quite shocked at the outcome.......continue
because it was marked as unsatisfactory but I was also quoted just under £500 including VAT to get the work corrected. The flat...
Electrician and electrical issues? Do you need to be qualified?
I had my kitchen gutted and fitted with a new kitchen. We had a few issues with the electrics/wiring. It was all done through...
Acceptable faults on Electrical Installation Condition Report
We rent a local building for children's community activities, and our landlord has given us notice from the end of September,...
A lot of electrical work needs doing - full rewire/safety inspection?
Hi everyone, I am looking for advice on electrical work I need done on our 4 bed detached property. The house is probably...
Post your job to find high quality tradesmen and get free quotes
- All Questions
- Architectural Services
- Bathroom Fitting
- Carpentry & Joinery
- Carpet & Lino
- Central Heating
- Chimneys & Fireplaces
- Conversions - General
- Damp Proofing
- Demolition & Waste Clearance
- Fascias, Soffits & Guttering
- Gas Work
- Groundwork & Foundations
- Hard Flooring
- Kitchen Fitting
- Landscape Gardening
- Loft Conversions
- New Builds
- Painting & Decorating
- Restoration & Refurbishment
- Security Systems
- Tree Surgery