Ask a tradesman
Vent-axia bathroom extractor fan constantly running
Hi. I had a Vent-Axia Silhouette Lo-Carbon extractor fan (model 441626 - 100HT( humidistat and timer) installed. The brown wire connected to L, the black connect to N, and the grey connect to LS. The fan is constantly running even when the light switch is off. It is not connected to a pull cord. Does anyone have a solution? Thanks for your time.
2 Answers from MyBuilder Electricians
Accrington • Member since 16 Dec 2010 • 33 jobs, 100% positive feedback
Either humidity is at a constantly high level, the unit is faulty or it is wired incorrectly. If this is not enough information for you then you will need to post for an electrician to diagnose/rectify the problem.
Answered 4th Oct 2015
There can be a number of reasons your fan is permanently on.
The installer may have the switch live and permanent live the wrong way round, (you can't always go with the correct colours at the fan as they may be wired incorrectly at the light switch or isolator switch, he would have to test this before terminating the conductors to find this out).
It could also be that the room is just very damp / humid, hence the fan seems to be constantly on.
Lastly it could be worth adjusting the extractor fan time and humidity sensor pots to lower the length of time the fan is on and to lower the humidity sensitivity.
Hope this help!
Answered 4th Oct 2015
Can I have a normal wall fan (not extractor fan) installed in my bathroom (zone 3)?
Hi thanks for the response. To clarify it is not a fan heater or extractor but just a fan as you might have on your desk. We have...
mould around bathroom extractor fan (water trickling down extractor pipe)
Started noticing mould this winter. The previous extractor fan was quite an old one and out of use, and had it replaced a couple...
Bathroom extractor fan: inline centrifugal through ceiling/tile vent, or axial fan through wall?
Hi Folks, I hope to glean some advice before getting an electrician in to install a bathroom extractor fan. Any advice would be...
bathroom extractor fan working with light
Hi, I used to have a old Manrose (DF100TLK,220-240v,50Hz,20W) inline fan with 12 volt light in the bathroom, it would come on...
Post your job to find high quality tradesmen and get free quotes
- All Questions
- Architectural Services
- Bathroom Fitting
- Carpentry & Joinery
- Carpet & Lino
- Central Heating
- Chimneys & Fireplaces
- Conversions - General
- Damp Proofing
- Demolition & Waste Clearance
- Fascias, Soffits & Guttering
- Gas Work
- Groundwork & Foundations
- Hard Flooring
- Kitchen Fitting
- Landscape Gardening
- Loft Conversions
- New Builds
- Painting & Decorating
- Restoration & Refurbishment
- Security Systems
- Tree Surgery