Ask a tradesman
Can we use 1.5mm flex for a dedicated washing machine and dishwasher circuits?
We're going to add 2 dedicated radial circuits, one for the dishwasher and one for the washing machine. Can we use a 1.5mm flex cable for this installation?
Additionally, we've got 2 spare 32A RCBO's. Can they be used for the same purpose or should they be replaced by smaller units, e.g. 16A?
What is the risk of using a 32A RCBO?
1 Answer from a MyBuilder Electrician
Very poor design to use 1.5mm flex for a radial circuit. It maybe possible to use it, but you will need to do your adiabetic equation to calculate the voltage drop on the cable based on the length of run at full load. If you don't have a copy of BS7671:2008 to hand you can get one from ebay or buy a new copy (approx. £70 from Amazon). 1.5mm flex is totally unsuitable for a BSEN60898 32amp MCB and 16amp MCB's must be used.
A far better solution would be to wire the circuit properly using 2.5mm cable.
Before you start any work, you will need to apply to your local authority and pay to apply for Part P building regulation consent to carry out the DIY electrical works (approx. £300). The local authority will need to come and inspect and test the work once completed and check that it meets the full requirements of BS7671:2008. depending on the inspector, you may have a job convincing them that 1.5mm flex is adequate!
Answered 1st Jul 2015
There's a "spare" drain/grid outside; Can I use it, and relocate the kitchen sink?
I've absolutely no clue about plumbing, drainage etc... Anyway. Currently, the sink and washing machine are connected to a water...
When we moved to our flat, the washing machine was in the bathroom. We bought a new one and Curry's wouldn't install in the bathroom (understand why) so it was set up in the kitchen (fittings existed)
now we want to install a dishwasher in the kitchen and move the washing machine back to the bathroom. Before I post a job, I'd...
Is it acceptable to do work for a client that has not been agreed and then demand payment?
I have just had a kitchen fitted by a general builder who I had used previously for one job. This gentleman had gained my trust...
My dishwasher and washing machine aren’t draining and are causing a leak. What is advised?
We had a new dishwasher installed a couple of days ago, along with a ‘floplast dual sink and wash trap’ to connect both...
Post your job to find high quality tradesmen and get free quotes
- All Questions
- Architectural Services
- Bathroom Fitting
- Carpentry & Joinery
- Carpet & Lino
- Central Heating
- Chimneys & Fireplaces
- Conversions - General
- Damp Proofing
- Demolition & Waste Clearance
- Fascias, Soffits & Guttering
- Gas Work
- Groundwork & Foundations
- Hard Flooring
- Kitchen Fitting
- Landscape Gardening
- Loft Conversions
- New Builds
- Painting & Decorating
- Restoration & Refurbishment
- Security Systems
- Tree Surgery