Ask a tradesman
Problems with a cable
I was wondering if someone could help this is a bit of a weird one.
I have a cable than runs through one side of a chimney breast in the living room and underneath the hearth to four sockets in my living room. The only reason I know this is because the fireplace was empty when I moved in and I had a log burner installed and a the hearth taken up and replaced about 6 months ago. The cable is protected by heat boarding and obviously the hearth. This evening I was watching tv and the tv/sky box kept losing power and every time it happened I'd hear a banging sound from under the hearth (fire hasn't been on for over a week now so don't think heat was contributing to it). I've now plugged the tv etc into other sockets not serviced by that cable and all is ok so not a problem with the equipment. My worst nightmare is having to get the fireplace ripped out to fix it so my question is, if I get an electrician over, can he effectively kill the cable in the fireplace currently servicing the sockets and feed a new one in from somewhere else? Appreciate he would probably be a need to channel into the walls to do this but I'd prefer that to ripping the fire out/ripping up my new floors and then potentially having to do it all over again if the same thing happens in future.
Any advice greatly appreciated!
2 Answers from MyBuilder Electricians
An electrician should have no problem isolating the cable at the back of another socket, it sounds as though the weight of the wood burner has damaged the insulation, the bang was a short from live to earth, did the breaker trip off?...if it didn't you have something else to look into. it should be no problem to chase into the walls to re-route the cable.
Answered 26th Mar 2015
This is a tricky one to solve without causing a mess.
Yes, you can run a new cable from one place to the other, however, you will need to go down into the floor then back up again, or up into the ceiling and back down again...!
Either way it's not ideal, it just depends which you'd rather have to repair afterwards...
Answered 26th Mar 2015
I have a light spuring off a plug socket (via a fuse). What size cable would I need to run from the fuse to the lights please? Would it be normal lighting cable or ring main cable?
Would I need any specific lights - I'm just worried that I'd have a greater voltage running through a socket spur compared to the...
we have a garage that has a room above it and its attached to the house we are having problems with damp, its a very cold room that isn't used don't think extension was done correctly any suggestions?
average size garage room above has a flat felt room steps go down into the room from the house was done years before we bought...
Do I need a fused spur or is a plug with a fuse ok?
Hi, I've just bought a nuaire PIV system (glorified fan) to go in the loft and it says it should be connected to a switched fused...
Can you replace a bathroom basin that has a full pedestal, with a basin that has a semi Pedestal ?
I have a small, fully tiled bathroom..(the tiles are from top to bottom, and without a skirting board). I currently have a basin...
Post your job to find high quality tradesmen and get free quotes
- All Questions
- Architectural Services
- Bathroom Fitting
- Carpentry & Joinery
- Carpet & Lino
- Central Heating
- Chimneys & Fireplaces
- Conversions - General
- Damp Proofing
- Demolition & Waste Clearance
- Fascias, Soffits & Guttering
- Gas Work
- Groundwork & Foundations
- Hard Flooring
- Kitchen Fitting
- Landscape Gardening
- Loft Conversions
- New Builds
- Painting & Decorating
- Restoration & Refurbishment
- Security Systems
- Tree Surgery