Ask a tradesman
Suitable size cable for 170 meter long temporary extension?
I need to fit temporary power to a fridge and freezer in a hut 170m from my mains? What size and type of cable can I get away with?
2 Answers from MyBuilder Electricians
If it is just to power up a refrigerator then 2.5mm 3core SWA will most certainly do the job. Allowing a voltage drop of 4.3%. Maximum allowed on lighting circuits is 3%, on anything else is 5%.
Answered 8th Feb 2016
you need to know the total load, the length, how it is run (clipped, buried, etc.), what type of cable. surrounded by insulation? grouped with other cables?
It= In/ Ca X Cg X Ci X CC
Volt drop cannot be more than 4/3%
Volt drop = mV X Ib X cable length/ 1000
Answered 28th Jan 2015
What cable size is for 9kw fryer?
Hi, I need some help with the cable size please. Basically, just want to know what cable size should be used with a 9kw fryer and...
Foundation for extension
Hi all. My foundation for extension size of 13.5 meter long and 1metres deep and 40cm weighed. Please if any answer to help me...
Cable size for garage connection
I have a detached garage which has a consumer unit with 4 separate circuits. This unit is connected to the main consumer unit in...
Cable size for automated gate, future new kitchen + Jacuzzi
I am having my driveway redone and want to install an automated sliding gate with motor of 0.6 - 0.8 KW and lights on the pillars....
Post your job to find high quality tradesmen and get free quotes
- All Questions
- Architectural Services
- Bathroom Fitting
- Carpentry & Joinery
- Carpet & Lino
- Central Heating
- Chimneys & Fireplaces
- Conversions - General
- Damp Proofing
- Demolition & Waste Clearance
- Fascias, Soffits & Guttering
- Gas Work
- Groundwork & Foundations
- Hard Flooring
- Kitchen Fitting
- Landscape Gardening
- Loft Conversions
- New Builds
- Painting & Decorating
- Restoration & Refurbishment
- Security Systems
- Tree Surgery