Ask a tradesman
How to fit pull switch (i have 2 red and 2 black wires from ceiling)
Can anyone help please, I have removed old fixture and have four wires in total. 2 red and 2 black.
My new fixture has scope for 4 connections. They are L1. L2. C and the 4th has a symbol showing three horizontal lines of differing lengths with one line at right angles to longest horizontal line ( I think that one is for the earth wire but I don't have an earth wire).
Can you tell me where I need to connect the 2 black and the 2 red cables please?
3 Answers from MyBuilder Electricians
Chances are the two blacks bypass the switch and should be in a choc blok the two reds would then go into l1 and c
Answered 26th Jan 2015
Leicester • Member since 21 Jan 2015 • 5 jobs, 100% positive feedback
My advice is if you don't know what your doing don't touch it, leave it to the professionals.
Answered 27th Jan 2015
You have bought a single pole 2 way ceiling switch and need a double pole switch. On a double pole switch red goes in the L terminals either side and black goes in the N terminals either side. (one set of red and black on L & N either side of the switch that has four terminals). On the switch you have the terminal with three stripes is the earth terminal and is for the green and yellow earth cable. If you have no earth present at the switch, then its likely to be old wiring (pre-1967, and may well be at the end of its working life and need completely rewiring). - Avoid DIY and get a professional in, as it will be safer.
Answered 28th Jan 2015
How much work do I need to do to be 'Satisfactory'
In order to satisfy my home insurance company, I recently had a NICEIC inspection on my recently purchased house (that I will be...
Wiring a pull cord light switch with two cables.
my bathroom ceiling light and pull cord switch were replaced and now the light won't come on at all. There are 6 wires in total. 2...
Advice what tool or drill I will need to make holes into ceiling to fix a Ceiling Gym Pulley mount.
I have a corded electronic Black&Decker 500w hammer drill which I have used to try and drill the correct holes in the ceiling to...
3 black wires in ceiling rose, which is L and N?
2 part question Replacing front room light. I didn't notice until I went to put up new light that there are 3 black wires - 2...
Post your job to find high quality tradesmen and get free quotes
- All Questions
- Architectural Services
- Bathroom Fitting
- Carpentry & Joinery
- Carpet & Lino
- Central Heating
- Chimneys & Fireplaces
- Conversions - General
- Damp Proofing
- Demolition & Waste Clearance
- Fascias, Soffits & Guttering
- Gas Work
- Groundwork & Foundations
- Hard Flooring
- Kitchen Fitting
- Landscape Gardening
- Loft Conversions
- New Builds
- Painting & Decorating
- Restoration & Refurbishment
- Security Systems
- Tree Surgery