Ask a tradesman
Electricians self certified work does not seem to comply?
I had a new kitchen extension 3 years ago and the electrics was done by a qualified pro who gave me the required certificate. For various reasons I've been reading up on the "regs" and have been very surprised by some of the latest requirements but the more I read the more I think "My kitchen isn't done like that!".
For example all the cables to the new kitchen run from the consumer unit through the hall in plastic trunking just above the skirting board. There is no RCD in my old consumer unit and those circuits just have standard MCBs like the rest. Some of the old cabling is in plastic trunking on the surface but in those days it was allowed without an RCD.
The lack of RCD seems to be a big issue yet I have the all important paperwork.
Two questions really, does it matter and is it common for electricians to certify work that they know doesn't comply?
Thanks for the reply NYE! Once it gets to the kitchen it is behind plasterboard.
So if it's all in trunking it's OK is it? I thought it had to be buried deep or protected?
2 Answers from MyBuilder Electricians
Hi there if the cabling from your consumer unit is as you say in trunking or surface mounted throughout its run and is not chased into a wall at any point then you do not need RCD protection. If it is chased into the wall then this would not be compliant and should have been RCD protected and assuming your kitchen is wired as a ring circuit you would of required a fuse board change to comply with current regulations.
Ok well once it goes behind the plaster board it then does need to be RCD protected it.
Answered 13th Jan 2015
I take it the kitchen in the extension has sockets?
All sockets added now require RCD protection whether cable is surface mounted or not.
Simple really - you should of had RCD protection.
Answered 15th Jan 2015
- Recently had self cleaning skylights fitted to loft. Bird muck fell on it three months back and still remains with other dirt. Self-cleaning doesn't seem to work. Any suggestions for fixing problem?
- How do you remove black grout that has been on slate tiles for about 8 weeks. I tried to use grout remover from Toppstiles, but this does not seem to work.
New consumer unit does not comply with current standards
Hello, I have recently bought a house and had a trader recommended by a friend to install a new consumer unit/fuse box. As he...
Builders guarantee for a large self-contained extension?
Hi there, My parents are now near to completion on a large self-contained extension, which is really a one bedroom flat attached...
Post your job to find high quality tradesmen and get free quotes
- All Questions
- Architectural Services
- Bathroom Fitting
- Carpentry & Joinery
- Carpet & Lino
- Central Heating
- Chimneys & Fireplaces
- Conversions - General
- Damp Proofing
- Demolition & Waste Clearance
- Fascias, Soffits & Guttering
- Gas Work
- Groundwork & Foundations
- Hard Flooring
- Kitchen Fitting
- Landscape Gardening
- Loft Conversions
- New Builds
- Painting & Decorating
- Restoration & Refurbishment
- Security Systems
- Tree Surgery