Ask a tradesman
New spotlight bar accepts two cables, but existing florescent bar light contains 6
I'm curious to know why there are three fat cables, each with two smaller cables inside, attached to my existing florescent bar light, but the new spotlight bar I have only takes two little cables (I assume live and neutral).
2 Answers from MyBuilder Electricians
Yes, the three cables currently at the light are the feed in, feed out, and switch line. You probably will see all the reds together in a connector block. This is how it needs to stay. Then in the N of the old fitting will be two blacks/blue, and in the L will be a black (should be sleeved or overlapped red/brown) or a brown. You need to take the florescent down keeping a note of what is the N and L, then just put new fitting up, the reds still all in a connector, the earths in the earth terminal the two blacks in the N terminal and the sleeved black into the L terminal. Hope this helps
Answered 7th Jan 2015
Hi you have three pairs of (fat) cables coming into the fitting both have red/brown and black/blue.
One comes from the supply which will be red/brown = live and black/blue = neutral –
One goes on to the next light which will be red/brown = live and black/blue = neutral –
One will come from the light switch the red/brown is live to the switch and the black/blue is live return from the switch (which should have some red/brown tape/sleeving on it letting you know its live) so when the switch makes the live returns up the black/blue cable which makes the light work.
Therefore the three reds are common and are connected together two blacks/blues go to the neutral and one black/blue goes to the live.
The trick is identifying the switch wire, if it hasn't got any tape/sleeve on it it might be turned over on the end.
If you haven't taken it apart yet mark the black/blue cable on its own that will be the switch live connect that to live.
All of the remaining black/blues connect in the neutral.
All of the reds are common and get connected together not to the fitting.
Hope this helps you get your head around it. :)
Answered 10th Mar 2017
LV lighting in large-ish room
NOTE: I will be getting an electrician to do the wiring work; but this might read like a DIY job because I've been trying to plan...
I wired additional fluorescent light to existing light in garage and it won't turn off
I wired additional fluorescent lighting to an existing light in my garage. The existing light was on one light switch. After...
Fit new PIR light into existing outdoor light circuit
Hi - I have an existing switch that controls two outdoor lights (1x wall mounted and 1x standalone). Is it possible to replace the...
Fitting a rectangular spotlight bar over a round ceiling rose hole
I have removed an old strip light from the kitchen ceiling, and there was a round back box underneath. The new spotlight bar has a...
Post your job to find high quality tradesmen and get free quotes
- All Questions
- Architectural Services
- Bathroom Fitting
- Carpentry & Joinery
- Carpet & Lino
- Central Heating
- Chimneys & Fireplaces
- Conversions - General
- Damp Proofing
- Demolition & Waste Clearance
- Fascias, Soffits & Guttering
- Gas Work
- Groundwork & Foundations
- Hard Flooring
- Kitchen Fitting
- Landscape Gardening
- Loft Conversions
- New Builds
- Painting & Decorating
- Restoration & Refurbishment
- Security Systems
- Tree Surgery