Ask a tradesperson
Shower goes from hot to cold - changed thermostat in shower bar, worcester combi serviced last year
The water starts of hot then goes really cold, thought it was the thermostat in the shower bar so I had it replaced but nothing has changed. I have a Worcester combi boiler only serviced last year.
3 Answers from MyBuilder Heating Engineers
Hello, firstly I'm not a qualified plumber but do allot of basic plumbing and hopefully I can help.
I think your Shower has an anti scald valve which over time they scald up and corrode and stop working well. One way to check is to flush the toilet nearest your shower or sink while the shower is running and see if the water changes temperature. If it does I think that's your problem .
I'm pretty sure they can be changed.
I hope this helps , and apologies if I'm way off the mark .
Answered 20th Sep 2014
Hi, just a quick check of your domestic water temperature may help. Your hot water needs to be set to 60 c lor less, sometimes the thermostat in the shower valve may open and close for protection. Also it may be an idea to install a combi mate valve to your shower feeds.
Hope this helps
Answered 22nd Sep 2014
Urmston,Manchester • Member since 1 Mar 2019 • 80 jobs, 99% positive feedback
If you have already changed your thermostatic shower cartridge and you still have intermittent hot water, it will be your boiler fault, if a combi it can be the secondary heat exchanger partially blocked , or temperature sensors on your boiler.
Answered 13th Feb 2020
Single shower impelled - Hot water only coming out of small shower head, not big shower head
Hello, We have installed a thermostatic shower rail to our shower room. The shower rail has a big shower head (which is fixed...
Increasing shower pressure: hot water from combo boiler, cold from loft tank
The current setup I have in my bathroom is: hot water coming from a combo boiler supplied from the mains; cold water coming from a...
PROBLEMS WITH MIXER TAP, SHOWER RUNS HOT THEN FREEZING COLD
I have a combi boiler Potterton Performa HE. A few months ago my mixer tap on my old Victorian style shower mixer stopped working,...
No water to shower after trying to turn from hot to cold mid shower
Hi I was trying to change to cold water mid shower and the water stopped, the shower motor is still working I think as it’s...
Post your job to find high quality tradespeople and get free quotes
- All Questions
- Architectural Services
- Bathroom Fitting
- Carpentry & Joinery
- Carpet & Lino
- Central Heating
- Chimneys & Fireplaces
- Conversions - General
- Damp Proofing
- Demolition & Waste Clearance
- Fascias, Soffits & Guttering
- Gas Work
- Groundwork & Foundations
- Hard Flooring
- Kitchen Fitting
- Landscape Gardening
- Loft Conversions
- New Builds
- Painting & Decorating
- Restoration & Refurbishment
- Security Systems
- Tree Surgery