Ask a tradesman
Relocating a gas pipe !??!
i wish to open a new doorway into my kitchen from my hallway but the gas pipe runs right infront of where my doorway would be so need to be moved ....the gas pipe is in use and fuels my boiler ...does anyone know whether the pipe could be moved underground or whether it would have to be run around the doorway ?...and also any ideas on cost .thankyou.
2 Answers from MyBuilder Gas Engineers
Southsea • Member since 8 Nov 2010 • 231 jobs, 99% positive feedback
The above response is correct / installtion / pricing.
However in addition consideration should be take as to the number of new bends that will be installed in the pipe-work diversion.
As the pipe is feeding the boiler it is essential that the correct gas pressure is maintained.
Incorporating bends into pipe-work effects the flow rate and therefore a new pipe-work calculation nedds to be carried out.
It may well be that the existing pipe is oversized and adequate to incorporate another few bends.
However it may be that the pipe-work is already on it's limit and therefore may need upgrading, at least in part, to allow for the additional bends.
Answered 20th Jul 2011
Bournemouth • Member since 9 Sep 2009 • 12 jobs, 100% positive feedback
You can divert the gas pipe to under the floor under channelled into concrete as long as it is sheathed properly.
Depending on type of floor and length of run will depend on the cost, but rough guide £45.00 per hour labour plus materials.
Hope this is helpful
Pipe Dreams Plumbing Services, Bournemouth
Answered 19th Jul 2011
Post your job to find high quality tradesmen and get free quotes
- All Questions
- Architectural Services
- Bathroom Fitting
- Carpentry & Joinery
- Carpet & Lino
- Central Heating
- Chimneys & Fireplaces
- Conversions - General
- Damp Proofing
- Demolition & Waste Clearance
- Fascias, Soffits & Guttering
- Gas Work
- Groundwork & Foundations
- Hard Flooring
- Kitchen Fitting
- Landscape Gardening
- Loft Conversions
- New Builds
- Painting & Decorating
- Restoration & Refurbishment
- Security Systems
- Tree Surgery
- Fitting a Gas cooker / gas supply to it + a few more gas related question
- Im fitting a kitchen with a gas range cooker in an island unit. The floor is concrete. What is the correct way to get a gas supply to the cooker. Im not doing the gas work myself.
- Can a gas hob and a seperate gas oven both run off one gas inlet.
- New Boiler - can I have a new boiler fitted if there is a a small gas leak?