aAsk a Tradesman
- Need some tips or advice?
- Post a Question
upstairs radiator not working - all others are ok - valve on one end Therm controller on other - took a spanner to valve and ensured open - still will not come on - what could the problem be?
- Yspanishrob 7th Dec, 2011 Plumbing
- share this question:
u 22 Like
On the thermostatic valve undo the ring which holds it onto the radiator, either by undoing the little screw or by unscrewing the retaining ring itself. Pull the valve off
and you will reveal a little silver plunger like a pencil lead about 1cm in size. Push this
plunger into the valve a few times to free it. The plunger getting stuck is often the problem. Then put the valve back together again. You should be able to feel the warm water coming into the rad as you waggle the plunger in.
- photofinish contracts 7th Dec, 2011
u 14 Like
Try taking the thermostatic head off and tapping the pin underneath. It is a very common problem that these pins stick. Have the heating on and keep tapping it firmly, but not too hard and you should find the rad getting hot.
Hope this helps.
- Diamond 7th Dec, 2011
u 10 Like
hi,there,s one way of finding out the problem,have central heating on and turn all working radiators off ..just leave the offending radiator on..failing that the trv valve is stuck in the off position,usually if you can remove the thermostatic top,no water will leak out..and just tap the spindle in the centre of the valve and off it goes..put the top back on..
- PAT THE PLUMBER 7th Dec, 2011
u 8 Like
you could have an air lock. Turn all other rads off and this should shift air lock.
- RD Services Ltd 7th Dec, 2011
u 3 Like
Pin stuck on thermostatic valve?
- PAUL CATON GAS SERVICES 7th Dec, 2011
u 3 Like
get a bleed valve key and open the bleed nipple at the top of the rad at one end,and let the air out .
- crest installations and maintenance services 7th Dec, 2011
u 3 Liked
Is the radiator old? been in the property for years? could be a build up of sludge in heating circuit or a balancing issue turn the flow into other rads down a bit to allow circulation to extend up to the problem rad.
I would first try to bleed top problem rad,
Then i would shut a couple of rads off down stairs for the time being and check the problem rad to see if it improves regarding heat performance.
Allow a few hours to see if the heated water gets through to the upstairs rad.
I have seen this many times and it is just a patience thing in getting the heating system balanced.
If not get the system power flushed.
Try shutting off 2 lower floor rads first as this will allow distribution to by pass the bottom rads and deliver to rest of circuit reaching top rad.
Concept building services
- Concept building services 7th Dec, 2011
u 1 Like
Someties thermostatic valves jam shut call someone to free it off
- sovereign plumbing and heating 7th Dec, 2011
- Top floor radiator not heating up fully - please help a girl in need........... Ydiy_dame 21st Dec, 2014
- Radiators not warming downstairs (system is open vent with a y plan valve) Ygareth_177 20th Nov, 2014
- Bleed Valves Three Port Valve Advice Please Ydiydiydiy_34 21st Nov, 2012
- Boiler sounds like its got boulders in it, had to turn system off. Engineer failed to fix problem Ymelany55 24th Jan, 2014
- All Questions
- Architectural Services
- Bathroom Fitting
- Carpentry & Joinery
- Carpet Fitting
- Chimneys & Fireplaces
- Conversions - General
- Damp Proofing
- Demolition & Clearing
- Garages & Sheds
- Gas Work
- Groundwork & Foundations
- Central Heating
- Kitchen Fitting
- Landscape Gardening
- Loft Conversions
- New Builds
- Painting & Decorating
- Restoration & Refurbishment
- Security Systems
- Tree Surgery